Plumbing Questions? Ask a Plumber and Get Answers ASAP.
Hi my name is Gary, i am here to answer all of your plumbing questions. After the question process is complete please hit accept, Thanks
you changed the faucet
did you check the pressure at the valve before reinstalling the faucet?
are your pipes galvanized? copper? or plastic?
from hot water tank they are galv. but they go into ceiling and walls, under sink they are 1/2 inc copp. butt they go into the ground. i live on the 1st fir.
Ok if you changed the faucet the problem is in the hot water line to this sink, galvanized pipe is bad for closing over from corrosion this is why we do not use much of it anymore
did you have a pressure problem on the hot before the faucet change or is this why you changed it in hopes to fix this problem?
yes then i changed the valve under sink
the problem is the galvanized pipe ive removed tons of it for same problem, If you had no pressure before its the old lines when you pull them out they are usually down to less then a pencil size in the middle from corrosion, you just need to replace them with copper or plastic on this and eventually all lines that are still galvanized im sorry to say, but you can do them as they start to plug up one at a time
eventually rust will start to wash up in your aerators and toilet fill valves but you could start with just replacing the problem line in this kitchen
so ther is nothn i can do to unclog it with galv. pipe still ther
not the pipe itself, now sometimes when we cut into a galvanized pipe with a sawsall to make a repair and the pipe gets banged around alot , rust from inside the pipe breaks lose and washs up and cloggs aerators and valves they then can be taken apart and cleaned but from what you tell me you had no pressure before and changed faucet and valve also its copper under the sink so you working on those lines would not break anything loose
So im sorry to say you just have to replace the galvanized line to restore pressure
sob! thank u sir.
sorry your welcome
If thats all i can do for you please hit accept, and thanks for using justanswer good luck with your project