Have HVAC questions? Ask an HVAC Expert for answers
Sounds like either connections are not making good or you have a failing board.clean and secure connections.Then with a multi meter put leads on wires to gas valve.If the 24v is dropping out, replace board.If 24v is constant issue is the valve.
If you have further questions, please let me know.
Thanks for letting me work with you.If my answer has been polite, professional,and thorough, please click one of the ratings before you go. If you still need help let me know!.Expert is not paid for assisting you until you rate answer.Feel free to follow up for 30 days at no additional cost. Bonus always appreciated if you feel justified.
To rate answer, please select one of the stars on the page.