Have HVAC Questions? Ask an HVAC Expert for Answers
Hi I am Gaztech1, a independent technician, I will assist you with your issue.
Don't forget to rate the 5 star rating AT THE TOP OF PAGE after we are done. this will credit me for assisting you.
Have cleaned the outside condenser with a hose to remove polen and dirt?
OK, and while unit is running is the biger of the 2 copper lines at the outside unit sweaty and cold,?
Means the compressor is not working, if may be a bad start capacitor, is the fan running of outside unit?
Humidity and heat will not get better if the compressor is not running. again, while outside fan is turning, the bigger copper line needs to be cold and wet???
Probably just a bad capacitor