Have HVAC Questions? Ask an HVAC Expert for Answers
Hello, it looks like we got our wires crossed here
I am an actual live HVAC technician, if you can give me the brand and model number of the equipment involved, tell me where it is located in the home, and about how old it is, we can go from there
check for 120 v to the condenser fan motor, it you have it there then the fan motor is bad, or its run capacitor is bad.
If you do not have power to the two wires that feed the condendser fan motor when the compressor is running then the problem is with the printed circuit board that has the condenser fan relay on it.
Attach a close up photo of the wiring diagram glued to the inside of the blower access door and I will mark it up with trouble shooting instructions then follow up with step by step training and coaching until you have a solution.
Photo must be exceedingly well focused. Use the 'add files ' link next to your send button to get the photo to me.