Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can continue our conversation.
This is usually caused by excessive pressure which is the result of thermal expansion of the water in the tank as it heats up. Excessive cold water pressure can contribute to the problem. The first things to do are to check the cold water pressure (should be 75 psi or less) and replace the relief valve. If the problem returns you'll need to install a thermal expansion tank.