Have HVAC Questions? Ask an HVAC Expert for Answers
Do you have a meter to see if we are getting power to the igniter?And can you look to see if it is burned or broken?
If you prefer phone conversation the site charges an extra fee, just accept offer.If not we can continue here.
It wlll be just in front of the first burner. If you can give me full model from label inside I may have a picture
That appears to be ac coil.I need
complete model from inside furnace in burner compartment so I can provide guidance with this specific unit.Model will be on a label just above burners on right or left inside panel
Give me a second to grab a manual
See link for location in front of first burner
OK Rheem used the spark instead of glow bar on some of these. Do you have a volt meter so we can see if gas valve is getting 24v when it sparks?
That is our next step is to see if board is sending 24v to valve.If you can find meter great, if
not you can get an inexpensive one at Walmart for about 15 bucks if you would like to troubleshoot and I would be happy to guide you.
Yes locate the 2 wires to as valve.Put one lead on each terminal. set to volts ac and see if we get 24v when igniter sparks.
2. Gas valve is where we want to check for 24v when ignitor sparks
my name is Billy.
Are you ready to test the terminals?