Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can
continue our conversation.
It sounds like you have a bad board maybe a bad gas valve. You need to test for 24 vac at the gas valve while the ignitor is glowing. If you have 24v at the valve when the igniter is glowing but no ignition and the valve only opens after the igniter goes out then you have a faulty gas valve. But if you don't get voltage to the valve until after the igniter goes out then the board is suspect.
Hi, do you still need assistance? Thanks
I have notified customer service, I apologize for your troubles