Have HVAC Questions? Ask an HVAC Expert for Answers
The 3 blink code indicates that the pressure switch is not closing.The first thing that happens on call for heat is the small vent motor(inducer) should come on and pull a vacuum on the pressure switch closing it.
So our first step is to verify the inducer vent motor is indeed coming on.We will go from here
Glad you got it working.
If you have further questions, please let me know.
Thanks for letting me work with you.If my answer has been polite, professional,and thorough, please click one of the ratings before you go. If you still need help let me know!.Expert is not paid for assisting you until you rate answer.Feel free to follow up for 30 days at no additional cost. Bonus always appreciated if you feel justified.
To rate answer, please select one of the stars on the page.