Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can continue our conversation.
This is a millivolt system. The pliot flame sensor (thermopile) generates all the power to operate the gas valve. It does this by maintaining a cold junction (temp diffential) between the tip (in the flame) and the "cold" bottom of the sensor. If a stray main burner flame heats up the cold junction the voltage drops out. A weak thermopile (they do "wear out") can also be the cause.