Have HVAC Questions? Ask an HVAC Expert for Answers
Can you give me complete model from inside furnace in burner compartment so I can provide guidance with this specific unit.Model will be on a label just above burners on right or left inside panel
That is fine, but to do any troubleshooting it will be necessary to go back to unit
Does the vent inducer motor actually come on?
When you can go back down, lets try something and that will tell us if it is on the vacuum side or drain side. Remove hose from inducer and leave attached to switch. After inducer starts, suck on hose to close switch.Keep sucking.keeping a vacuum on switch.See if furnace will stay running.If so we need to concentrate on why we are not getting enough vacuum.If not concentrate on drain.
Let me know if furnace will stay running while sucking on hose
That one has a bit different set up. not sure which hose you would need to draw a vacuum on. I am going to open to other experts who may know.
Yes will send to admin.