Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can continue our conversation.
The first thing to check is the pressuretrol. It's pretty common for the piping connecting the pressuretrol to the boiler to clog with rust. So cleaning it out is always the first thing to try. Could also be a balky end switch in the motorized vent damper which has to prove the damper is open before the ignition process can proceed. Is the damper opening when it doesn't fire up?
Do you have more questions?