Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can continue our conversation.
They should close as soon as the steam hits them. If they're blowing steam then the pressure on the boiler is probably set too high. The pressure range on a residential boiler should be 1 to 3 psi. Most air valves are only rated to 5 psi