Have HVAC Questions? Ask an HVAC Expert for Answers
Make sure door button is pushed in and see if you get any power to board
Using a volt meter test wires where they first enter furnace for 120v
Check between LINEH and LINE-N on board for 120v
Then unplug th 12 pin plug from board and check for 24v between red and blue
Sent both are you not getting them?
Make sure door switch is pushed in
OK check from Line N to the other side of door switch
Show me on diagram where you had 124.6 Volts
OK I drew them using RED and GRAY
Power is coming into the Junction box between Red and Gray
Does it come in and out of junction box?
Yes, just connect the wires together coming in and out of the switch
THat does not make sense.If you have power to door switch, connect wire from other side of door swirth you should have power.
Fuse should not come into play as far as having voltage on both sides of switch.
OK going into furnace but not between LH and L-N?
Can you send a photo and then describe in photo where you have power?
If you have a paper clip icon on your page you can attach using that link.Or
You can upload the pictures using the tiny pic site .
Here is a link to the site.
Click on Browse , select the file from your folder.then click UPLOAD NOW.
They will give you a quote to enter in the box to verify you are a human.Enter the quote and click UPLOAD NOW
You will see your picture on right side of screen.
Then copy the link URL for email & IM
Paste that link here on the site.
Great now if nor lights are on check that fuse
Auto parts stre will have one if you have an auto parts store close
If you have further questions, please let me know.
Thanks for letting me work with you.If my answer has been polite, professional,and thorough, please click one of the ratings before you go. If you still need help let me know!.Expert is not paid for assisting you until you rate answer.Feel free to follow up for 30 days at no additional cost. Bonus always appreciated if you feel justified.
To rate answer, please select one of the stars on the page.
t me know if that fixes you up.