Have HVAC Questions? Ask an HVAC Expert for Answers
Sounds like we may not be getting 24v to contactor.Do you have a multi meter so we can troubleshoot?
Next check 230v in and out of contactor
Do you have 230 to 240 on both sides of contactor as shown above?
OK so we have power in and out of contactor to compressor and motor but neither will come on and breaker does not trip?
OK if you are sure everything is wired properly, capacitor is reading within range but nothing come son the compressor and fa would have to be defective. It is not unusual to get a DOA capacitor, Have you checked it?
Can you verify 230v between the fan wires ? And same with compressor (Common and RUN)?