Have HVAC Questions? Ask an HVAC Expert for Answers
Red wire to R (may say rc or rh)
green wire to G
Purple - not used
blue - O/B
yellow - Y
white - Aux
orange - not used
Sorry took so long...it took a while to cross ref.
Did you receive the information?
you likely did not set the dip switches yet for remote thermostat.
If you want warning lights you can go ahead and and hook up L
Also the dip switches ans wiring are covered in the tech manual HERE
did you read the tech manual I sent you link of?
Looks like L is (LS) and not needed anyway for lights..it is a building management feature.
The dip switches are shown on page 39...do you need the manual link again?
It is not to read...page 39 has pictures of where the dip switches are and what they do..like the remote/thermostat dip switch. It must be set to off.
I have given the engineering manual with designation of terminals, pictures iof the board with dip switches...
I cannot supply anymore than that...I will see if someone else here can assist you better.