Have HVAC Questions? Ask an HVAC Expert for Answers
There is one item that will cycle a unit like this.
It is a low pressure switch. When the unit kicks on the pressure is dropping ....eventually it trips a low cut off and then shuts down...once the pressure builds back up and equalizes the unit kicks back on...it does this over and over.
You will need the refrigerant level checked. If it were high pressure it would not kick back on by itself...
You are very welcome...given the safety circuit it is the only item that can cycle according to the run times you supplied.
Anything else would be more sporadic come and go failures. This will be directly related to low pressure.
OR...the low pressure switch itself is bad.