Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can continue our conversation.
If the main blower won't start the the unit will overheat and shut down with the error you indicate. You need to determine if you have power to the blower motor 45 seconds after the burners ignite. If you have power then you could have a bad start capacitor or a bad motor. If you don't have power to the blower then the board probably needs to be replaced.