Have HVAC Questions? Ask an HVAC Expert for Answers
What is question. Russ
This is a pressure switch error. Is the small fan in burner compartment running. Sequence should be small induce fan starts---pressure switch closes--igniter glows-- gas valve opens. Make sure small fan starts russ. Let me know.