Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can continue our conversation.
You have to purge the line with the burner running. Assuming you have the bleeder on the burner pump open, you have to hold the reset button down for 30 seconds to bet the burner to restart after a hard lockout (2 attempts with no flame). If your ignition control is a Beckett not a Honeywell then you hold it down for at least 15 seconds
Pump bleeder pic attached