Have HVAC Questions? Ask an HVAC Expert for Answers
hi i am dan i can help you with this, first lets start at the beging what was the original problem? was it smoking before you changed the filter and nozzel?
ok did you check the flow from the tank to make sure the line is not cloged and did you replace the strainer, how long did you wait after filling the tank before you started the burner?
did you check it out of the nozzle line, if not i would check that it should be a steady stream until it locks out.
was the flow out of the nozzle line good?
if you were not getting any sputtering from the nozzle line the flame should not be sputtering, does the flame cut out? did it get good pressure out of the nozzle line? it should be a really strong stream.
and was the flame sputtering or does it rumble alot?
what nozzle was in there before and did you replace it with the same nozzle, same gallons angle and patern?
it is not smoking now and running good?
it is possible that there may have been alot of excess oil in the chamber from before that takes some time to burn off but i would like to make sure you have the correct nozzle in there. what was the angle of the old one and angle of the new one
Did you have any more questions? If not I would appreciate it if you could rate me on my service by selecting one of the 5 stars and thank you for using just answer