Have HVAC Questions? Ask an HVAC Expert for Answers
hi i am dan i can help you with this. first is the new board installed now or the old board?
ok and what was the problem when the new board is installed that it wont heat or the heat doesnt turn off?
ok i assume you mean the switch for the blower door and what is the status of the led lights on that board when the fan continuously runs
ok are you able to take a picture of the circuit board installed showing all the wiring connections and post it here. that would be a lot easier for me to see what is going on and help you diagnose it.
instructions for attaching files
i have not got anything. you have to attach them to your post
ok got it. give me a minute to review them
ok first i see alot of incorect wiring conection so i will mark it up for you to correct but it will take some time. no need to reply as the system requires a response from me every time you post but i will get back to you in a few minutes
yes and you do not have an electric air cleaner for a filter correct?
ok that is fine
ok as i said you do not need to reply as it requires a response from me
i have drawn up the corrections for the wiring. if you can correct this wiring and install the board securely where the old board was and change the dip switches as i have marked the way they should be set and install a 3 amp fuse and turn the furnace back on we can see if it works now or continue troubleshooting from there. i will also send you a phone call offer if it will be easier for you to explain it over the phone or if you have any questions about the wiring just reply back here.
They are not potted. It is just tamper tape over it so the factory knows if it was used when returning. Just push it with a small screwdriver or meter leed.
Ok let me know
is your furnace still not working or did that fix it?