Have HVAC Questions? Ask an HVAC Expert for Answers
So far it sounds like you put the original card back, I have never seen a new card produce such a wide range of errors.
Tell me how thoroughly you dried out the molex connectors and roll out switches etc, We can go from there.
If indeed it is a new card, you will need a good multi meter with a uA (micro amp scale) on it, use it to measure the amperage flow from the end of the flame sensor wire to the printed circuit card when flames are impinging on the flame sensor rod... you might want to clean the flame sensor rod off with a scotch brite pot scrubber pad first.
We can go from there.
It is not advisable to post your phone number or email address to this forum, it is publicly available on google you might get crank calls.
The company needs extra money for phone calls, it runs up their quality control costs... so far I do not thing a call is necessary however.