Have HVAC Questions? Ask an HVAC Expert for Answers
Hello, there are 6 LED lights...so from LEFT to right which ones are lit...Just type O for not lit and X for lit like this OOXXOOO
OK great, that is a ignitor code, most times you may have a bad ignitor or it is broken. You need to remove the burner to get at it and check it out and see.
1 Check wiring to the hot surface ignitor - replaceignitor assembly if wiring is damaged or worn.2 Check ignitor assembly plug and the socket on theIntelli-Vent™ body for good connection. Replaceignitor assembly and/or control if necessary.3 Check resistance of ignitor at room temperature(77°F) at the plug end. Replace ignitor if resistance isnot within 11.5 and 18.8 ohms at room temperature.4 If results from the above tests were good and errorcode 5 persists - replace the Intelli-Vent™ control.
All I ask is please rate my service using the star link on your page thanks!