Have HVAC Questions? Ask an HVAC Expert for Answers
Why is my heat pump/air conditioner leaking water onto my basement floor? I assume it is condensate since the puddle is not that large. My unit is many years old, installed when the house was built in 1993. I changed filters but am not sure I have the right size. I took out 25 x21 x1's but can only find 25 x 20's in local hardware//bigbox stores. Help.
Hi,Most likely, it is indeed condensate as you suspect.It may be one of several things.
Is there an auxiliary drain pipe?You may have to open the air handler door and inspect the drain. There should not be much water in the pan (a little). If it is deep your drain is either restricted or not properly trapped. If it's metal, look for rust, if it's rusty, it may just need a new drain pan. You really can't see the part of the coil that would get dirty, it would be on the incoming air inlet side of the coil.
It sounds like it could be the drain. The water seems to collect around the base of the unit and does not appear to be dripping from the refrigerant line. Have no idea if there's an auxiliary drain - I view this thing as a magical metal box that heats & cools the house without much interference from mortals! But it has been quite a while since any service was done on the unit so it may be time to call in a local technician. At least I now have some idea of what problems I am having and can ask intelligently for repairs. I thank you for that.
If you can see the end of the drain (maybe it goes to a floor drain). You can try to attach a shop vacuum to it and see if it pulls a bunch of goop along with the water. Sometimes that does the trick.
No floor drain visible - house is built on a floating slab. No shop vacuum. You are dealing with a technically inept grandmother. But another thought to have in mind for a repair person.
A technician uses a device called a gallow gun. Think of one of those CO2 cartridges used for whipping cream or in some pellet guns. They use this to blow the drain out.I would probably suggest getting it serviced while it's only a small problem. Use a reputable HVAC service company and if you don't know any ask your friends and family. The yellow pages are full of "hacks" and "cheats".