Have HVAC Questions? Ask an HVAC Expert for Answers
Billy, Hello. I had it secured it properly also all 3 contactors, cond fan motor & both pressure switches were replaced prior to me visiting this call in last few months.. Is there any other tips i also picked up new control board which i wanted to change but was holding
Billy hello Again . Hope u had great day. I did figure out problem with ur help & tips./
Replaced all 3 contactors still it was blowing fuse after combing through wires blower fan relay gave clue traced wires n found wires from wiring harness going to economizer were exposed n touching blower housing i guess from vibration repaired wires unit is working one happy customer.
Regards XXXXX XXXXX You