Electrical

Electrical Questions? Ask an Electrician Online.

Electrical

# I wish to add an standard duplex outlet to a Kichler

Customer Question
Hi - I wish to...
Hi - I wish to add an standard duplex outlet to a Kichler Lighting Power Supply Hardwire 50w Cabinet Accessory in Black 12353BK, via the next run in the space inside the 12353BK. What are the requirements to keep this in electrical code given that the future duplex outlet will not be in a wall, but will be attached via single gang box.
Submitted: 1 year ago.Category: Electrical
Show More
Show Less
11/14/2016
Electrician: Kevin, Licensed Electrical Contractor replied 1 year ago
Category: Electrical
Satisfied Customers: 3,952
Experience: 31 years Licensed Electrical Contractor in Illinois, Adjunct College Electrical Instructor, Former Electrical Inspector, Diploma: Digital Electronics, FCC Technician License
Verified

Hello and welcome to Just Answer. My name is ***** ***** I will be happy to assist you with your electrical question.

1) Receptacles are always required to reside inside a box.

2) Are you looking to tap off of the Kichler power supply to provide 120 volts to a receptacle?

Customer reply replied 1 year ago
Hi Kevin -
1) Understood on the first point - I'm trying to make sure if I have to place the 12/2 wiring in a PVC or equivalent to get to a box.
2) Correct - tap off the Kichler power supply to provide 120 Volts to a duplex outlet. With the planned duplex, I will still be under 10 outlets total for the circuit breaker.Thanks!
Michael
Electrician: Kevin, Licensed Electrical Contractor replied 1 year ago

Thanks for the replies Mike.

1) Adding another receptacle onto a 15 or 20 amp breaker is not an issue.

However, the power supply is only 50 watts which is designated for the lighting. By tapping off of the power supply, there may be insufficient wattage available for a plugged-on load. Watts Law is P = I x E. Solve for I. 50 watts/120 volts = .41 amps.

Hope this helps………If you have any additional questions, just let me know and I’ll be glad to answer them for you.

Otherwise, don’t forget to rate me before you log Off.

Thanks.................Kevin:)

Customer reply replied 1 year ago
as there are two of the 12353BKs, on the top part of a cabinet, separated by approximately 5 and 1/2 feet - am I allowed to run 12/2 from the first to second, or do I need to run this through some type of PVC? I want to make sure I am staying in code ... both 12353BKs currently their own dedicated wire run so I'll simply re-terminate one of them into a remodeling box and 20A duplex outlet.Thanks!
Electrician: Kevin, Licensed Electrical Contractor replied 1 year ago

1) The 12/2 NM Romex cable needs to be protected by either installing the cable inside conduit or box the NM Romex cable and protect it by using wooden furring strips. Either method will be code compliant.

Category: Electrical
Satisfied Customers: 3,952
3,952 Satisfied Customers
Experience: 31 years Licensed Electrical Contractor in Illinois, Adjunct College Electrical Instructor, Former Electrical Inspector, Diploma: Digital Electronics, FCC Technician License

Kevin is online now

A new question is answered every 9 seconds

• Ask an ExpertExperts are full of valuable knowledge and are ready to help with any question. Credentials confirmed by a Fortune 500 verification firm.
• Get a Professional AnswerVia email, text message, or notification as you wait on our site. Ask follow up questions if you need to.

Ask-a-doc Web sites: If you've got a quick question, you can try to get an answer from sites that say they have various specialists on hand to give quick answers... Justanswer.com.
...leave nothing to chance.
Traffic on JustAnswer rose 14 percent...and had nearly 400,000 page views in 30 days...inquiries related to stress, high blood pressure, drinking and heart pain jumped 33 percent.
Tory Johnson, GMA Workplace Contributor, discusses work-from-home jobs, such as JustAnswer in which verified Experts answer people’s questions.
I will tell you that...the things you have to go through to be an Expert are quite rigorous.

## What Customers are Saying:

You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future.

JimmyBagley, IA

Wonderful service, prompt, efficient, and accurate. Couldn't have asked for more. I cannot thank you enough for your help.

Mary C.Freshfield, Liverpool, UK

This expert is wonderful. They truly know what they are talking about, and they actually care about you. They really helped put my nerves at ease. Thank you so much!!!!

AlexLos Angeles, CA

Thank you for all your help. It is nice to know that this service is here for people like myself, who need answers fast and are not sure who to consult.

GPHesperia, CA

I couldn't be more satisfied! This is the site I will always come to when I need a second opinion.

JustinKernersville, NC

Just let me say that this encounter has been entirely professional and most helpful. I liked that I could ask additional questions and get answered in a very short turn around.

EstherWoodstock, NY

Thank you so much for taking your time and knowledge to support my concerns. Not only did you answer my questions, you even took it a step further with replying with more pertinent information I needed to know.

RobinElkton, Maryland

< Previous | Next >

## Meet the Experts:

Mike

Master Electrician

1,426 satisfied customers

Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer

Jason

Service Technician

3,942 satisfied customers

Over 20 years of experience in all types of installations, troubleshooting, and repairs.

Mike G.

Master Electrician

7,826 satisfied customers

Proven Professional 48 years Experience

Kevin

3,952 satisfied customers

31 years Licensed Electrical Contractor in Illinois, Adjunct College Electrical Instructor, Former Electrical Inspector, Diploma: Digital Electronics, FCC Technician License

AssuredElectrical

Master Electrician

3,264 satisfied customers

electrifier

Master Electrician

1,458 satisfied customers

Electrical contractor and electrical inspector for over 24 years with phone and networking expertise

Rich

Master Electrician

1,115 satisfied customers

Over 35 years residential, commercial, industrial wiring, install, troubleshoot, service, maintain

< Previous | Next >

Related Electrical Questions
I checked all circuit breakers to see if any tripped. I
Hi, I checked all circuit breakers to see if any tripped. I reset all of them and checked voltage. They are all receiving power. So I changed the 2 outlets that went out on the side of one room. Still… read more
Kevin
3,952 satisfied customers
I have a problem with a circuit breaker tripping fairly
I have a problem with a circuit breaker tripping fairly regularly. I believe I have too many plugs on one circuit. How can I check to see if I have too many on one breaker. I have done a lot of wiring… read more
George Smith
321 satisfied customers
My microwave flips a circuit breaker when I turn it on. It's
my microwave flips a circuit breaker when I turn it on. It's in the same location, same outlet, same everything. The outlet works with other things, like vacuum, elec light. The microwave works perfec… read more
Kevin
3,952 satisfied customers
Circuit breaker blew switch. Switch is not resetting. Just
Circuit breaker blew switch. Switch is not resetting. Just kinda dangles there, with no tension to either side. How can I fix this?… read more
Sam I
Electrician
B.S.
474 satisfied customers
The circuit breaker hasn't popped but in living room non of
The circuit breaker hasn't popped but in living room non of the 4 outlets are working. Checked the 4 plugs for any signs of loose wires or spark marks. ? What's next? … read more
Kevin
3,952 satisfied customers
I am trying to replace an outlet. Red wire backstabbed high.
I am trying to replace an outlet. Red wire backstabbed high. Black wire back stabbed low. Black wire looped to screw low. My new outlet only has screws, no back stabs … read more
Kevin
3,952 satisfied customers
Can a General Electric type THQL-GCI hot tub circuit breaker
can a General Electric type THQL-GCI hot tub circuit breaker be tested with an ohm meter. … read more
Kevin
3,952 satisfied customers
How do I determine the correct size circuit breaker panel
How do I determine the correct size circuit breaker panel for an stand alone workshop. I don't suspect I would draw more than 20 amps at any given time, but do I need a box assumes everything is turne… read more
Mike G.
Master Electrician
7,826 satisfied customers
Wiring diagram for outlet on a switch the to a light on same
wiring diagram for outlet on a switch the to a light on same switch … read more
David Bowden
Owner
469 satisfied customers
What is the function that makes a circuit breaker different
what is the function that makes a circuit breaker different from a switch so that it is able to break fault current … read more
Kevin
3,952 satisfied customers
Question on wiring GFCI outlet... Late 80's...and no. Outlet
outlet is under the sink...bottom outlet goes to switch on the wall… read more
Sam I
Electrician
B.S.
474 satisfied customers
Was wondering which circuit breaker I should look into
Hello, was wondering which circuit breaker I should look into replacing. As it stands my Dryer flips the circuit breaker for the upstairs bedrooms. Should I look into replacing the circuit breaker for… read more
Kevin
3,952 satisfied customers
My circuit breaker is tripped and will not reset. I've
My circuit breaker is tripped and will not reset. I've checked wiring to outlets looks okay. At the electrical panel there is no power to breaker itself. I check other breakers and the have power. Any… read more
Eddie
Home Improvement Contractor and Repairs
High School or GED
1,048 satisfied customers
I have a well pump wired into a 240v/20a circuit breaker. C/
I have a well pump wired into a 240v/20a circuit breaker. C/B has white wire, black wire, ground wire. Pressure switch on well pump has same...black, white. ground. Output from pressure switch to pump… read more
Electrical Contractor
564 satisfied customers
I've checked ALL circuit breaker with a voltage meter. They
I've checked ALL circuit breaker with a voltage meter. They are good, but I still don't have power in both bathrooms. Not in the outlets or ceiling lights. Can you help. … read more
Kevin
3,952 satisfied customers
The circuit breaker tripped controlling all the electricity
The circuit breaker tripped controlling all the electricity in my son's bedroom. This circuit also controls the recessed lighting in the dining room. The only way I can reset the circuit breaker is if… read more
Mike G.
Master Electrician
7,826 satisfied customers
Need help determining wire size, wire type, and conduit size
Need help determining wire size, wire type, and conduit size for 200amp panel with a 200 amp subpanel. Here is a list of my questions: http://mnjustin.com/diagram.jpg… read more
Mike G.
Master Electrician
7,826 satisfied customers
What size wire is needed to run underground in conduit to a
What size wire is needed to run underground in conduit to a garage about 60 feet from the main connection at the power pole? This would be connected to a subpanel in the garage. … read more
Kevin