Trying to install a new light fixture where there used to be a florescence light
- has black on bottom and white on top
And ground to the switch
Ceiling box - has two black and one white Together all with that are "hot
Also there are 3 wires free /
-one black wire that is hot a
- one white wire that is hot
-oone white wire That "not "hot
I tried hooking caped hot" the black and white wire together With the Black wire from the fixture to be black and white "Hot"
And caped white "not hot" coming out of the ceiling
To the new fixture white
it registered hot with my dummy stick but when I went to the rest of the outlets
they also registered hot
When I went to plug in a A light it did not work.
My outlet tester it registered hot and ground reversed
Not sure what I'm doing wrong?