Electrical Questions? Ask an Electrician Online.
Hi, I'm Mike G and I'll be assisting you. You are correct
The underwater light should be on its own circuit as the blower should be. You'll need to trace the wiring to verify they are. In doing so check for any water infiltration which could cause GFCI trips.
One more thing, an underwater light should not be on a circuit shared with anything else. The receptacle and the blower connections are a code violation.