Electrical

Electrical Questions? Ask an Electrician Online.

Electrical

# 7.5 kw heat at 208 volt 3 phase equals how many amps

7.5 kw heat at 208 volt 3 phase equals how many amps
10/23/2012
Jason, Service Technician
Category: Electrical
Satisfied Customers: 4,289
Experience: Over 20 years of experience in all types of installations, troubleshooting, and repairs.
Verified

Jason :

Jason :

This calculates to about 36 amps.

Jason :

That being the case, I would feed it with a 50 amp breaker, and #6 copper wire.

Jason :

If you are using THHN stranded building wire, it can be #8/

Customer:

can you provide the formula that you used

Jason :

Sure. Volts X Amps = Watts. We know the wattage is 7500, and the voltage is 208. So, just divide the watts by the volts, 7500/208 to arrive at 36 amps.

Customer:

watts divided by volts--x 1.732 equals amps correct ??this is 3 phase

Customer:

are u there

Jason :

Thank you for your patience. I'm referencing my materials, as it's been a while since I had to determine when to use the 1.73 rule.

Jason :

Yes, you are correct. I was mistaken. 36 X 1.73 = 62.28. That would be a 70 amp breaker and #4 copper wire.

Customer:

ok---explain this:

Customer:

7500 watts at 240 volt SINGLE phase is 31.25 amps (watts divided by volts)---7500 watts / 208 volts=36.06 times 1.732 is= 62.46 amps----shouldn't the amperage on 3 phase be lower than single phase ???

Jason :

Now that I look at it again, I believe we are both misapplying the formula.

Customer:

what am i doing wrong ?

Jason :

We don't need to multiply the original amperage I arrived at by 1.73.

Jason :

That is to find watts.

Jason :

Wire is sized on amperage, not wattage.

Customer:

a 7.5 kw heater at 208 3 phase

Customer:

7.5 is 7500 watts

Jason :

Yes

Customer:

so only 7500 divided by 208 ??

Jason :

Yes.

Customer:

ok--thanks

Jason :

I apologize for being rusty, it's been a while since I've had to use the 1.73 rule.

Customer:

gues im done--nite

Jason :

If you don't mind standing by for a moment...

Jason :

I just found a site that explains it very well.

Customer:

so i just close this web site now ?

Jason :

I'll post a link after I view it.

Customer:

ok--go i go now ?? dinner is waiting

Jason :

You can go and come back later. No problem.

Jason, Service Technician
Category: Electrical
Satisfied Customers: 4,289
Experience: Over 20 years of experience in all types of installations, troubleshooting, and repairs.
Verified
OK, here's a site that explains it well...

So, according to this info, you need to first multiply your voltage by 1.73. That comes out to about 360 volts. Then, divide your wattage by that number, which comes out to just over 20 amps.

So, I would run #10 wire, and put this on a 30 amp breaker.

Jason, Service Technician
Category: Electrical
Satisfied Customers: 4,289
4,289 Satisfied Customers
Experience: Over 20 years of experience in all types of installations, troubleshooting, and repairs.

Jason is online now

A new question is answered every 9 seconds

• Ask an ExpertExperts are full of valuable knowledge and are ready to help with any question. Credentials confirmed by a Fortune 500 verification firm.
• Get a Professional AnswerVia email, text message, or notification as you wait on our site. Ask follow up questions if you need to.

Ask-a-doc Web sites: If you've got a quick question, you can try to get an answer from sites that say they have various specialists on hand to give quick answers... Justanswer.com.
...leave nothing to chance.
Traffic on JustAnswer rose 14 percent...and had nearly 400,000 page views in 30 days...inquiries related to stress, high blood pressure, drinking and heart pain jumped 33 percent.
Tory Johnson, GMA Workplace Contributor, discusses work-from-home jobs, such as JustAnswer in which verified Experts answer people’s questions.
I will tell you that...the things you have to go through to be an Expert are quite rigorous.

## What Customers are Saying:

You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future.

JimmyBagley, IA

Wonderful service, prompt, efficient, and accurate. Couldn't have asked for more. I cannot thank you enough for your help.

Mary C.Freshfield, Liverpool, UK

This expert is wonderful. They truly know what they are talking about, and they actually care about you. They really helped put my nerves at ease. Thank you so much!!!!

AlexLos Angeles, CA

Thank you for all your help. It is nice to know that this service is here for people like myself, who need answers fast and are not sure who to consult.

GPHesperia, CA

I couldn't be more satisfied! This is the site I will always come to when I need a second opinion.

JustinKernersville, NC

Just let me say that this encounter has been entirely professional and most helpful. I liked that I could ask additional questions and get answered in a very short turn around.

EstherWoodstock, NY

Thank you so much for taking your time and knowledge to support my concerns. Not only did you answer my questions, you even took it a step further with replying with more pertinent information I needed to know.

RobinElkton, Maryland

< Previous | Next >

## Meet the Experts:

Mike

Master Electrician

1,426 satisfied customers

Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer

Jason

Service Technician

4,289 satisfied customers

Over 20 years of experience in all types of installations, troubleshooting, and repairs.

Mike G.

Master Electrician

7,826 satisfied customers

Proven Professional 48 years Experience

Kevin

3,870 satisfied customers

31 years Licensed Electrical Contractor in Illinois, Adjunct College Electrical Instructor, Former Electrical Inspector, Diploma: Digital Electronics, FCC Technician License

AssuredElectrical

Master Electrician

3,264 satisfied customers

electrifier

Master Electrician

1,458 satisfied customers

Electrical contractor and electrical inspector for over 24 years with phone and networking expertise

Rich

Master Electrician

1,115 satisfied customers

Over 35 years residential, commercial, industrial wiring, install, troubleshoot, service, maintain

< Previous | Next >

Related Electrical Questions
I have a dual outlet wall receptacle with two sets of wires
I have a dual outlet wall receptacle with two sets of wires attached to it. I want to split this receptacle so that one outlet is controlled by a switch and add another unswitched dual outlet "downstream." Is this possible and if so, how should it be wired? Thanks. … read more
Kevin
Diploma
3,870 satisfied customers
I have a legrand dimmer switch that i installed replacing a
I have a legrand dimmer switch that i installed replacing a single pole non dimmer switch. I only had two wires on the old switch and they were unmarked. The wire i assumed was hot was the one coming … read more
Kevin
Diploma
3,870 satisfied customers
What is the code regarding GF I outlets in a bathroom? I
What is the code regarding GF I outlets in a bathroom? I know that an outlet near the sink must be protected but what about an outlet that is on the opposite wall from the sink in the bathroom. Is it … read more
Kevin
Diploma
3,870 satisfied customers
Installed a bathroom fan and the j-box of the fan has three
Hi Kevin, installed a bathroom fan and the j-box of the fan has three holes in it to connect wires to it. I opened all three but only used two of the holes for my wiring. I then put back the attic ins… read more
Kevin
Diploma
3,870 satisfied customers
I would like to bypass / eliminate a motion sensor from a
I would like to bypass / eliminate a motion sensor from a flood light circuit on outside of house … read more
Kevin
Diploma
3,870 satisfied customers
Electrician My daughter has used hair dryers in her bedroom
electricianMy daughter has used hair dryers in her bedroom and three of them have ended up smoking and going in a non working state.how can we stop this from happening? There are no other problems wit… read more
HVAC Guru
Service Technician
Associate Degree
682 satisfied customers
I'm replacing a 3 way switch this time except the switch has
Hey Sam, So I'm replacing a 3 way switch this time except the switch has more wires than expected. It has 3 black wires and 1 red wire. I have already wired it up but does not work. The light will onl… read more
Sam I
Electrician
B.S.
474 satisfied customers
I was told I had an electrical hazard in a rental because of
I was told I had an electrical hazard in a rental because of a outlet showing open ground, open neutral , open hot, hot and ground reversed, or hot and neutral reversed. I was told to correct it or re… read more
Kevin
Diploma
3,870 satisfied customers
The Leviton box with AT&T Battery is emitting 2 beeps every
The Leviton box with AT&T Battery is emitting 2 beeps every few minutes. Replace Battery light is on. This Battery has been in use less than 1 & 1/2 years. Should this Battery last no longer than that… read more
George Smith
320 satisfied customers
I am looking to see what controls I can change out on an
I am looking to see what controls I can change out on an electric radiant heating system in the ceiiling … read more
Mike G.
Master Electrician
7,826 satisfied customers
I am trenching 600 feet to cattle working pens and want to
I am trenching 600 feet to cattle working pens and want to bury wiring to supply power for lighting. What wire is best to use? It will not be carrying a heavy load… read more
Mike G.
Master Electrician
7,826 satisfied customers
I have a and 1 hp motor that I'm hooking up to a Bremas
I have a smith and jones 1 hp motor that I'm hooking up to a Bremas black handle switch. I need to know which wires go where. … read more
George Smith
320 satisfied customers
I have an electrical outlet that gets hot and smokes when I
I have an electrical outlet that gets hot and smokes when I plug in a t v . can I put new outlets in , will that help ? … read more
Kevin
Diploma
3,870 satisfied customers
My builder hard wired the ceilings for smoke detectors, but
Hi. My builder hard wired the ceilings for smoke detectors, but there is only one white wire and one red wire. What does this mean?I'm trying to install a nest smoke/carbon monoxide detector and it lo… read more
Mike G.
Master Electrician
7,826 satisfied customers
I installed a new ceiling fan to existing wiring, 1 variable
I installed a new ceiling fan to existing wiring, 1 variable fan control,1 fan light switch and another switch that controls a table light. That all seemed to work fine , now I am trying to hookup a d… read more
George Smith
320 satisfied customers
My son bought a house and found that the electrical outlets
My son bought a house and found that the electrical outlets in the kitchen are not working. What could the problem be and what do u recommend? Thanks… read more
Mike G.
Master Electrician
7,826 satisfied customers
I have a model IL-930 and want to replace it. What model
I have a model IL-930 and want to replace it. What model fits the same back plate and plug? … read more
Mike G.
Master Electrician
7,826 satisfied customers
I have a question regarding fan controls. A few days. Will
[Second opinion] I have a question regarding fan controls … read more
George Smith