Electrical

Electrical Questions? Ask an Electrician Online.

Electrical

# I have a 240 volt system for pool motor and pool sweep. In

I have a 240 volt...

Dennett Hanssmann [email protected]
Show More
Show Less
8/15/2011
Will, President & Small Business Owner
Category: Electrical
Satisfied Customers: 342
Experience: IBEW apprentice to Journeyman, 30 years experience Owner Operator
Verified

Will :

You asked a great question with very complete details,

Will :

you can't use 2 single pole GFCI CB's on a MWBC which is sharing a neutral. You certainly could use a 3-wire circuit with a 2 pole GFCI CB

Will :

When a GFCI is protecting a simple 120 volt circuit it monitors the current on the neutral and the hot as long as they are within about 5ma the GFCI will not trip.

When a GFCI is protecting a 240 volt circuit it monitors the current on both hots, as long as they are within about 5ma the GFCI will not trip.

When a GFCI is protecting a 120/240 volt circuit it monitors the current on the neutral and the two hots as long as they are within about 5ma the GFCI will not trip.

Will :

You seem to be very educated in electrical, you do need a 2 pole breaker, this is a hot topic many times over, so don't feel like your question or decision was out there, many argue over this question especially about differentials {if that would happen to be the case between the two poles if configuration of 120 volt loads were needed, and around a pool you want the best, XXXXX XXXXX to be double correct, pardon the pun, but since you can return the two for the one, should be no problem

Customer :

What is a mwbc?

Customer :

Oh, I bet it is multi-wire branch circuit?

Customer :

I gather that a 120V circuit is just one side, one or the other of the hot wires separated by 240V from each other, and by 120V from neutral. And, I gather that a 240V circuit is one that is just using the two hot wires to make the total 240V difference. But, what is a 120/240V circuit?

Will :

## Multiwire branch circuit definition & implementation

I am running a MWBC to an outbuilding. I want to qualify for Exception to 250.32, which allows NOT having a grounding electrode for the out-building provided it is a single branch circuit feeder (including MWBC). The supply is a 240v 3-conductor 10 awg, if it matters. There will be a cut-off switch at the outbuilding.

As for the actual circuitry within the outbuilding, I am wondering what the pros/cons are for running several 2-wire conductors from the cut-off switch (some on each hot wire --- i.e. some run from black feed, some from red feed) versus running 3-wire conductors to everything in the outbuilding.

It seems easier to me to run 2-wire from the switch as outlined above and divide the load that way. But, does that still constitute a MWBC from the perspective of the250.32 exception? (There is no fusing or circuit breakers in the outbuilding.) Is this acceptable? desirable? frowned upon?

Will :

this is one example of the confusion

Will :

and yes you are correct again,

Will :

To have both 120 and 240 volts at the shed or other separate building [whatever the situation] you must run one combination 120/240 volt circuit aka multiwire branch circuit. (It has two hots, one shared neutral, and one ground).

To have more than 20 amps of 240 volts or more than two 20 amp subcircuits of 120 volts you must have a subpanel out in the shed.

Will :

The problem comes from different interpretations of the NEC and too many DIY electrical problems, few know what you know, but run wire and plug things in all day, I also volunteer on allexperts.com and have for years, it is a wonder thousands don't burn buildings down each day, it is refreshing to hear from someone who actually asks intelligent questions you must have some kind of training,

Will :

I have another guy who just lost his reverse switch for his boat hoist but wants to direct wire the motor to get the boat out for visitors I have not heard from him in a while I told him to take the load off the motor, how to wire it, and now worry he is in between a boat and a hard spot,

Customer :

Okay, you may be getting a little beyond me. I have 2 motors, I think about 1hp each, and they would constitute almost all of the load for the subpanel. There are #10 in a 4 wire feeder from the service, and I'm presuming, then, I will wire with a ganged breaker, gfci, to these motors [via timers that control them]. So, is the ganged breaker labelled 240? (Not 120?) And, I'm presuming that the full load from the 2 motors, at 240V, should make 20A sufficient protection for the breaker rating? Yes, I used Richter's book years ago, and got a lot of help from LA County Building Inspection Dept. when re-wiring a house woefully under code, as the homeowner. Years of hobby of electrical stuff before that. But obviously my knowledge is spotty, and I don't want to screw this up. Is any of this wrong. Oh, there is an unbalanced load on the whole system at the subpanel, i.e. there's a 120V pool light, but that is upstream from the 240 gfci ganged breaker, and is a separate 120V gfci which will serve the pool light. So, I think if you just answer this last inquiry, esp. as to the ratings for the 240V circuit and it's breaker(s), that should do it. I think my account has \$45 in it, and I'll be happy to pay you that in entirety if, either now, or later, I see my way clear to a well-done job from your responses. Thanks so far.

Customer :

Reviewing the above, there should be a question mark after "Is any of this wrong(?)", and the pool light circuit isn't exactly "upstream" of the 240V 2 pole breaker, just on one of the same busses, as one side, and neutral on the other. So, from your description of how the gfci works, each breaker will be monitoring it's own imbalance, and there won't be any effect from the pool light drawing current from only one of the hot feeders.

Customer :

So, just to summarize my only further questions, I THINK!: 20A okay for the ganged breaker supplying at 240 V two 1hp motors? I can get the VA and current ratings on those motors, I think, from the nameplates, but I presume the hp ratings are enough for you. And, is the 240 the nominal rating, i.e. not 2 120 "sides" for the ganged breaker for those motors?

Customer :

I'm getting a bit tired, and may need to check out for now. Thanks for your help so far, and I'll check again in the morning if I don't stay present for your last response tonight. Is there a way to get back to you in case I want to pose further questions? Thanks for the help so far. I think I'd like to press "accept" so you are sure to be paid, but I'm still hoping for those last answers. I'll wait a few more moments, then hope to re-check here in the A.M. I'll press "accept" before I leave.

Will :

Will :

with a pool in my area and I have one, a 5 foot fence is demanded by my insurance, a 6 foot fence is not allowed as injury is more likely climbing a 6 foot fence versus a 5 foot, go figure

Customer :

I have a permit, and the thing will definitely be inspected before it is put to use. But these were the ratings on the previous breakers, and they virtually never tripped. They were not, except for the light, gfci, so this is an upgrade to the system. I'll ask the inspector(s) and be sure they're comfortable with it. If there's any question, I'll hire an electrician, which was what I had hoped to do online, but I understand your hesitation. Thanks, XXXXX XXXXX been very helpful.

Customer :

May I pay you, now?

Will :

You are welcome and great to hear you have the perfect plan, I think you are going to be just fine with those ratings, but virtually never tripped means what?

Customer :

Just that the ratings must have been reasonably generous and not too close to the actual current drawn by these motors. And the breakers that were in there were 20A.

Customer :

I do appreciate you efforts. Must go to bed. Let me know when I can press "accept" and I'll do it tonight, or, if I have to check out, I'll re-visit for that purpose in the next day or two, same spot online.

Will, President & Small Business Owner
Category: Electrical
Satisfied Customers: 342
Experience: IBEW apprentice to Journeyman, 30 years experience Owner Operator
Verified
Customer reply replied 6 years ago
Will,

You DO understand my circuit. So, the question I'm still asking is simply this: IS the breaker I want, regardless of amperage rating, a 240V, 2 pole (double breaker with handles tied together)? The puzzlement comes, I think, because, right or wrong, the OLD circuit just had two independent breakers, one on each hot side, and if either breaker were to trip, the circuit would be opened. And I think they may have been 120V each. They were NOT gfci, so there was no question about monitoring between a neutral and a hot vs. two hots. So, 240, 2 pole breaker? Thanks in advance.

Dennett H.
Rich, Master Electrician
Category: Electrical
Satisfied Customers: 1,801
Experience: Over 35 years residential, commercial, industrial wiring, install, troubleshoot, service, maintain
Verified

Hello .. yes you need a 2 pole breaker

is there a separate breaker for each motor? and one for the lights .. in that sub panel ??

please could you look on the name plates of the motors and post the amperage rating gs of each here .. Thanks

Will, President & Small Business Owner
Category: Electrical
Satisfied Customers: 342
342 Satisfied Customers
Experience: IBEW apprentice to Journeyman, 30 years experience Owner Operator

Will is online now

A new question is answered every 9 seconds

• Ask an ExpertExperts are full of valuable knowledge and are ready to help with any question. Credentials confirmed by a Fortune 500 verification firm.
• Get a Professional AnswerVia email, text message, or notification as you wait on our site. Ask follow up questions if you need to.

Ask-a-doc Web sites: If you've got a quick question, you can try to get an answer from sites that say they have various specialists on hand to give quick answers... Justanswer.com.
...leave nothing to chance.
Traffic on JustAnswer rose 14 percent...and had nearly 400,000 page views in 30 days...inquiries related to stress, high blood pressure, drinking and heart pain jumped 33 percent.
Tory Johnson, GMA Workplace Contributor, discusses work-from-home jobs, such as JustAnswer in which verified Experts answer people’s questions.
I will tell you that...the things you have to go through to be an Expert are quite rigorous.

## What Customers are Saying:

You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future.

JimmyBagley, IA

Wonderful service, prompt, efficient, and accurate. Couldn't have asked for more. I cannot thank you enough for your help.

Mary C.Freshfield, Liverpool, UK

This expert is wonderful. They truly know what they are talking about, and they actually care about you. They really helped put my nerves at ease. Thank you so much!!!!

AlexLos Angeles, CA

Thank you for all your help. It is nice to know that this service is here for people like myself, who need answers fast and are not sure who to consult.

GPHesperia, CA

I couldn't be more satisfied! This is the site I will always come to when I need a second opinion.

JustinKernersville, NC

Just let me say that this encounter has been entirely professional and most helpful. I liked that I could ask additional questions and get answered in a very short turn around.

EstherWoodstock, NY

Thank you so much for taking your time and knowledge to support my concerns. Not only did you answer my questions, you even took it a step further with replying with more pertinent information I needed to know.

RobinElkton, Maryland

< Previous | Next >

## Meet the Experts:

Mike

Master Electrician

1,426 satisfied customers

Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer

Jason

Service Technician

3,942 satisfied customers

Over 20 years of experience in all types of installations, troubleshooting, and repairs.

Mike G.

Master Electrician

7,826 satisfied customers

Proven Professional 48 years Experience

Kevin

3,870 satisfied customers

31 years Licensed Electrical Contractor in Illinois, Adjunct College Electrical Instructor, Former Electrical Inspector, Diploma: Digital Electronics, FCC Technician License

AssuredElectrical

Master Electrician

3,264 satisfied customers

electrifier

Master Electrician

1,458 satisfied customers

Electrical contractor and electrical inspector for over 24 years with phone and networking expertise

Rich

Master Electrician

1,801 satisfied customers

Over 35 years residential, commercial, industrial wiring, install, troubleshoot, service, maintain

< Previous | Next >

Related Electrical Questions
I have a and 1 hp motor that I'm hooking up to a Bremas
I have a smith and jones 1 hp motor that I'm hooking up to a Bremas black handle switch. I need to know which wires go where. … read more
George Smith
324 satisfied customers
I bought an automotive scissor lift Motor came with a short
I bought an automotive scissor lift Motor came with a short whip with three wires brown blue green and white stripe you're supposed to get extension cord to plug into wall 115 Extension cord is black … read more
Mike G.
Master Electrician
7,826 satisfied customers
I have a GE electric motor rebuilt with five black wires
I have a GE electric motor rebuilt with five black wires coming out with the following numbers 1 2 3 & 4&5 tighed together model # is 5KC49WG1181A HP 1 1/2 RPM 1725 HZ 60 PH 1 Code J ER 56A SF 1.0. A … read more
Sam I
Electrician
B.S.
474 satisfied customers
I have this compressor with the lr22132 motor, I had it
I have this compressor with the lr22132 motor , I had it temporary wired up . when I moved it to the shead 2 weeks later the motor wont operate I have electric in and out of the pressure switch. press… read more
Mike G.
Master Electrician
7,826 satisfied customers
I wired it up and ran motor without load no problem ... then
Mike,I wired it up and ran motor without load no problem ... then I put belt on compressor and started to run approx 1 minute into it — the motor started to smoke… read more
Mike G.
Master Electrician
7,826 satisfied customers
I have a GE compressor motor model 5KCR49UN2401Y. Can you
Hi, I have a GE compressor motor model 5KCR49UN2401Y. Can you tell me how to change wiring from 230 volts to 115 volts?… read more
Sam I
Electrician
B.S.
474 satisfied customers
I have a Dayton shutter motor model # 24N066 and I am
I have a Dayton shutter motor model # 24N066 and I am confused about which wires to connect together. They are all one on top of the other in the diagram. I am using the 120 V connection. … read more
Mike G.
Master Electrician
7,826 satisfied customers
I'm wiring a 230v compressor motor, and need to verify that
I'm wiring a 230v compressor motor, and need to verify that I have wires properly combined. I will provide motor information below. Thank youMake: Steveco Farm Duty Model: MS182C17FB2A Labeled Wires P… read more
George Smith
324 satisfied customers
Need a motor or motor/fan assembly for model 80213 exhaust
need a motor or motor/fan assembly for model 80213 exhaust fan/light … read more
Mike G.
Master Electrician
7,826 satisfied customers
I have a smith + Jones compressor motor. I need to know how
I have a smith + Jones compressor motor. I need to know how to wire it for 230v. It is model number D56 3S2C. I'm wiring it for 3hp compressor option CCW. I have 4 wires coming out of motor. T1 T4 T5 … read more
Mike G.
Master Electrician
7,826 satisfied customers
Trying to find a wiring diagram for a very old ge motor.
trying to find a wiring diagram for a very old ge motor … read more
Sam I
Electrician
B.S.
474 satisfied customers
I have a 3 phase 2 HP motor. It is a Lincoln e;ectric motor
I have a 3 phase 2 HP motor. It is a Lincoln e;ectric motor Model SSF4P2T61. Can I run this on single phase power, it seems to have the option on the label to run at either 60 or 50Hz and 230/460 V or… read more
HVAC Guru
Service Technician
Associate Degree
682 satisfied customers
I have a davit with a Leeson motor C6C17NC66A and a Salzer
I have a davit with a Leeson motor C6C17NC66A and a Salzer rotary switch. Someone yanked out the pigtail for incoming power and I can't find where to reconnect the black, white, and green. Any ideas? … read more
Sam I
Electrician
B.S.
474 satisfied customers
Trying to exchange lighting fixtures in Motor home. Just
trying to exchange lighting fixtures in Motor home … read more
Mike G.
Master Electrician
7,826 satisfied customers
Looking for Magnetek Universal Electric motor, ser.27ZA,
looking for Magnetek Universal Electric motor, ser.27ZA, 53930P Mod. DA 39142 115 60 950RPM 1BHP, or replacement … read more
Sam I
Electrician
B.S.
474 satisfied customers
The motor runs but there is no electrical power, About a
Sometimes the power comes back or for a while and then stops. its almost like there was a loose connection. i checked all the connections and power cord.… read more
Mike G.
Master Electrician
7,826 satisfied customers
Motor is on and turning but bladers are not. Just started
Motor is on and turning but bladers are not JA: I'll do all I can to help. How long have you been dealing with this? Customer: Just started JA: Do you plan on doing the work yourself? Customer: YES JA… read more
Sam I
Electrician
B.S.
474 satisfied customers
My timer is hook to my pool motor, and the motor loses
My timer is hook to my pool motor, and the motor loses power. Is this lack of electrical connections. It's trigger my main switch off couple of times. … read more
Sam I
Electrician
B.S.
474 satisfied customers
Disclaimer: Information in questions, answers, and other posts on this site ("Posts") comes from individual users, not JustAnswer; JustAnswer is not responsible for Posts. Posts are for general information, are not intended to substitute for informed professional advice (medical, legal, veterinary, financial, etc.), or to establish a professional-client relationship. The site and services are provided "as is" with no warranty or representations by JustAnswer regarding the qualifications of Experts. To see what credentials have been verified by a third-party service, please click on the "Verified" symbol in some Experts' profiles. JustAnswer is not intended or designed for EMERGENCY questions which should be directed immediately by telephone or in-person to qualified professionals.

Disclaimer: Information in questions, answers, and other posts on this site ("Posts") comes from individual users, not JustAnswer; JustAnswer is not responsible for Posts. Posts are for general information, are not intended to substitute for informed professional advice (medical, legal, veterinary, financial, etc.), or to establish a professional-client relationship. The site and services are provided "as is" with no warranty or representations by JustAnswer regarding the qualifications of Experts. To see what credentials have been verified by a third-party service, please click on the "Verified" symbol in some Experts' profiles. JustAnswer is not intended or designed for EMERGENCY questions which should be directed immediately by telephone or in-person to qualified professionals.

Show MoreShow Less