Electrical

Electrical Questions? Ask an Electrician Online.

Electrical

Is A Double Pole 30 Amp Breaker Two 15 Amp Breakers?

Customer Question
Is a double pole 30...

Is a double pole 30 amp breaker just two 15 amp breakers side by side; doubling the voltage? Or is it two 30 amp breakers side by side?

Submitted: 8 years ago.Category: Electrical
Show More
Show Less
8/10/2009
Electrician: Jason, Service Technician replied 8 years ago
Jason, Service Technician
Category: Electrical
Satisfied Customers: 4,289
Experience: Over 20 years of experience in all types of installations, troubleshooting, and repairs.
Verified

The amperage rating of the breaker is the number that is stamped on the breaker. If it says "15", then it's a 15 amp breaker. If it says "30", then it's a 30 amp breaker. In other words, you are not required to do any math to determine the amp rating for the breaker.

Since it is a double pole breaker, it is double the Voltage of a single pole breaker installed in the same panel. So, if your panel is 120/240 volts like a standard residential panel, then your double pole breaker is rated for 240 volts.

Customer reply replied 8 years ago

Here's the reason I asked: I have an old oven that I think draws 40 amps but it's fed by two linked single pole breakers marked 20 amps. Can that be? Should the individual breakers both be marked at 40 amps?

Electrician: Jason, Service Technician replied 8 years ago
a 40 amp breaker would be marked "40". If your oven is connected to a double pole 20 amp breaker, and it's an oven ONLY, with no cooktop on the same circuit, it's possible that it draws less than 20 amps. It should be marked somewhere with an amperage requirement, or you can use an amp meter to read the amperage drawn by the oven when it is on.
Customer reply replied 8 years ago
Thanks. So, in conclusion then -- whatever the amperage draw of a 110/220 appliance both individual breakers (if there were two indidual breakers linked instead of one one double pole) will be marked at that amperage. A forty amp oven would be fed by two 40 amp individual single-pole breakers or one 40 amp double pole breaker. Correct?
Electrician: Jason, Service Technician replied 8 years ago

That's correct. By the way, the electrical code only allows two single pole breakers to be used as a double pole breaker if they are linked by an "approved" handle tie.

Jason, Service Technician
Category: Electrical
Satisfied Customers: 4,289
Experience: Over 20 years of experience in all types of installations, troubleshooting, and repairs.
Verified
Jason, Service Technician
Category: Electrical
Satisfied Customers: 4,289
4,289 Satisfied Customers
Experience: Over 20 years of experience in all types of installations, troubleshooting, and repairs.

Jason is online now

A new question is answered every 9 seconds

• Ask an ExpertExperts are full of valuable knowledge and are ready to help with any question. Credentials confirmed by a Fortune 500 verification firm.
• Get a Professional AnswerVia email, text message, or notification as you wait on our site. Ask follow up questions if you need to.

Ask-a-doc Web sites: If you've got a quick question, you can try to get an answer from sites that say they have various specialists on hand to give quick answers... Justanswer.com.
...leave nothing to chance.
Traffic on JustAnswer rose 14 percent...and had nearly 400,000 page views in 30 days...inquiries related to stress, high blood pressure, drinking and heart pain jumped 33 percent.
Tory Johnson, GMA Workplace Contributor, discusses work-from-home jobs, such as JustAnswer in which verified Experts answer people’s questions.
I will tell you that...the things you have to go through to be an Expert are quite rigorous.

What Customers are Saying:

You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future.

JimmyBagley, IA

Wonderful service, prompt, efficient, and accurate. Couldn't have asked for more. I cannot thank you enough for your help.

Mary C.Freshfield, Liverpool, UK

This expert is wonderful. They truly know what they are talking about, and they actually care about you. They really helped put my nerves at ease. Thank you so much!!!!

AlexLos Angeles, CA

Thank you for all your help. It is nice to know that this service is here for people like myself, who need answers fast and are not sure who to consult.

GPHesperia, CA

I couldn't be more satisfied! This is the site I will always come to when I need a second opinion.

JustinKernersville, NC

Just let me say that this encounter has been entirely professional and most helpful. I liked that I could ask additional questions and get answered in a very short turn around.

EstherWoodstock, NY

Thank you so much for taking your time and knowledge to support my concerns. Not only did you answer my questions, you even took it a step further with replying with more pertinent information I needed to know.

RobinElkton, Maryland

< Previous | Next >

Meet the Experts:

Mike

Master Electrician

1,426 satisfied customers

Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer

Jason

Service Technician

4,289 satisfied customers

Over 20 years of experience in all types of installations, troubleshooting, and repairs.

Mike G.

Master Electrician

7,826 satisfied customers

Proven Professional 48 years Experience

Kevin

3,870 satisfied customers

31 years Licensed Electrical Contractor in Illinois, Adjunct College Electrical Instructor, Former Electrical Inspector, Diploma: Digital Electronics, FCC Technician License

AssuredElectrical

Master Electrician

3,264 satisfied customers

electrifier

Master Electrician

1,458 satisfied customers

Electrical contractor and electrical inspector for over 24 years with phone and networking expertise

Rich

Master Electrician

1,115 satisfied customers

Over 35 years residential, commercial, industrial wiring, install, troubleshoot, service, maintain

< Previous | Next >

Related Electrical Questions
I started hearing a buzzing sound from the ceiling of the
i started hearing a buzzing sound from the ceiling of the house. sounds electrical (also, it's at 50Hz, which I think is the UK mains AC frequency) … read more
Kevin
Diploma
3,870 satisfied customers
Installing a GFi receptacle in old where there is no ground
Installing a GFi receptacle in old where there is no ground wire. I can identify the hot wires on the line feed wires with a tester, but can identify the load wires since the are both dark. One looks … read more
Kevin
Diploma
3,870 satisfied customers
I have a mechanics question; please connect me to a
I have a mechanics question; please connect me to a mechanic! … read more
Leamon Rollo
16 satisfied customers
I recently changed an outlet to a new one with usb
I recently changed an outlet to a new one with usb connection. The outlet had 2 black and 2 white. The new outlet only needed 1 and 1. I taped the remaining wires and now the lights don't work in the … read more
Mike G.
Master Electrician
7,826 satisfied customers
I have a vintage wadsworth 60 amp main fuse panel pull=out
I have a vintage wadsworth 60 amp main fuse panel pull=out fuse holder inside my breaker panel, I recently lost power in a couple of rooms in my house , I replaced all the buss 60, 30 & 20 amp fuses w… read more
Mike G.
Master Electrician
7,826 satisfied customers
I have an Intermatic Model ST01 wall switch timer. After 3
I have an Intermatic Model ST01 wall switch timer. After 3 months or so, it started clicking on and off. I got a new one and it is doing the same thing. I wired it exactly how it was wired initially a… read more
George Smith
314 satisfied customers
Half the lights in the apartment I am renting go into a
half the lights in the apartment I am renting go into a pulsing mode once the switch is turned on for the fluorescent kitchen fixture that the landlord just installed. The breaker doesn't trip. None d… read more
Mike G.
Master Electrician
7,826 satisfied customers
My Craftmade TCS Fan/light control will not work. I've
My Craftmade TCS Fan/light control will not work. I've changed the batteries twice but it still will not work. What should the settings be on the ON Edge inside the remote? … read more
Leamon Rollo
16 satisfied customers
I have an electrical question. It's a new heater. Its just
I have an electrical question JA: How old is the system in question? And have you consulted an electrician yet? Customer: No. It's a new heater JA: Do you plan on doing the work yourself? Customer: Ye… read more
Sam I
Electrician
B.S.
472 satisfied customers
I spilt water over an electric socket which had a lamp
I spilt water over an electric socket which had a lamp plugged in and switched on. I moped … read more
George Smith
314 satisfied customers
Have a three phase delta grounded system. At the disconnect
have a three phase delta grounded system. At the disconnect with it turned off I read 275 to ground on all 3 phases but phase to phase read 3 volts..what do you think?… read more
Shane
Not Finished
0 satisfied customers
I have one switch box with a black, a red, and a wires. The
Hello Pearl, I am Jerry Shoemaker and I have one switch box with a black, a red, and a white wires. The other box (both have three way switches) has two blacks and a red. I've ID the "Hot" black wire … read more
Sam I
Electrician
B.S.
472 satisfied customers
I checked all circuit breakers to see if any tripped. I
Hi, I checked all circuit breakers to see if any tripped. I reset all of them and checked voltage. They are all receiving power. So I changed the 2 outlets that went out on the side of one room. Still… read more
Kevin
Diploma
3,870 satisfied customers
I recently bought several machines that came with a 220v to
i recently bought several machines that came with a 220v to 380v power converter and i would need some advice on how to hook it up since it didn't come with a wiring diagram. Have pictures available. … read more
Sam I
Electrician
B.S.
472 satisfied customers
I have a square-D CSED that I'm trying to wire. I am trying
I have a square-D CSED that I'm trying to wire. I am trying to wire the thing, but I don't exactly know how. I have SEU running into the top and will have SER cable out the bottom that will go over to… read more
George Smith
314 satisfied customers
I am replacing a ceiling fan with light with a new light fan
I am replacing a ceiling fan with light with a new light fan combo with a remote. I have two black wires, two white wires and one ground coming from ceiling and the fan recover is the remote and it ha… read more
Kevin
Diploma
3,870 satisfied customers
Have a red not hot, hot,black hot, and bare ground wire
have a red not hot,white hot,black hot, and bare ground wire coming to my cieling fan, which wires do i use? … read more
Mike G.
Master Electrician
7,826 satisfied customers
I am working on a Maytag microwave over the range model
I am working on a Maytag microwave over the range model number MMV5208WS-0. The microwave three months ago was not heating and I replaced the magnetron and diode. It worked for three months and now ha… read more
Leamon Rollo