how do i increase pressure in my boiler. System leak repaired but can't get pressure back, so no hot water, Boiler checked and is fine.Radiators won't fill either. I have opened all valves.
opened tap to refill boiler. Opened all valves on radiator and bled radiators.
Hi I am Rick, UK Plumber, and I specialize on Boiler problems, you will have a filling loop usually near the boiler, this consists of a braided flexi hose with a tap at one or both ends, connect this hose and turn on both taps to fill the system, it may not be near the boiler, but it will be in a place that heating a mains pipes are together, depending on your boiler you could have a model that has a built in filling system, you may have a "key" to operate it or just a pair of taps under the boiler, but for more detailed info on this I would need the make and model of the boiler, regards Rick
There's a key. It's a worcester Greenstar 37cdi combi. I've opened that tap, water goes through but pressure guage doesn't move. Boiler has been checked and it's fine. Engineer said there was leak in system and it's been found and repaired.
OK are you sure that the key is fully home before you turn it, you are turning the valve to the left of the key? you should hear the water flow, if the pressure is increasing then water should come out of the radiator bleed points indicating this pressure, if that is the case then it is probable that the boiler pressure gauge/sensor is clogged up/faulty, RickRick Ridley40419.365972419
yes, i can hear the water running into the boiler. The engineer checked the pressure guage and said that it was fine. If I open the radiator blled point, nothing happens.
I added to my last post but maybe you did not see it, you are opening the valve to the left of the key, Rick
sorry, didn't see it!
yes i am.
If you are not able to bleed the rads it would suggest that nothing is going into the system or that the system is empty and needs more water that you have so far put in, was the system drained to cure the leak? Rick
yes, the system was drained. How long would it take roughly to fill the system? Also, should I open all the radiator valves at once? There are 3 floors. Does it fill from the bottom up?
All the radiator valves should be open, continue filling until you get a reading a reading of around 2 bar on the gauge, then bleed the rads keeping an eye on the pressure, and topping up as required, although it sounds like a lot of water is flowing it is not that fast, and can take a while to fill, Rick
Thanks. I'm going to do that. I did try yesterday but I had the bleed valve open also.
Maybe i didn't try for long enough.
Can I just see how this goes or should I 'accept answer' and come back if nothing happens?
See how it goes, I will be about most of the day, off and on, wait to hear, Rick
sorry I'm not sure if I sent this so apologies if it's the second time.
I spent the day with the tap open and apart from the sound of water going into the upstairs radiator, nothing has happened. Pressure hasn't come back up and radiators haven't refilled. It can't take this long can it?
No, are you sure you have not got a leak some where, water is clearly going into the system, have you checked the pressure relief valve discharge point out side the house, Rick
nothing coming out of the overflow. No signs of water in the house so I think that only leave under the ground floor. I can't hear anything but it must be there.This much water would have shown up elsewhere.
It might be easier to ask a plumber to just put new pipe under the floor rather than lift the floor up.
If it has been running all day you will need your wellies for under the floor, hope you get it sorted soon, I know it is the obvious but is there a drain point under the floor that has not been done up, it would not be the first time a plumber has forgotten that, Rick
30 Years on the tools, now retired, Ex CORGI
I don't think so as it's been fine for a couple of years and would have shown up before. I hope the whole floor doesn't need to come up.
Many thanks for all your time today. I'll send this then hit the'accept' button.
Glad to have been of service, Rick