UK Appliance Repair Questions? Ask a Technician for Answers ASAP
If it's marked 16 amp it would be around 3.6kw.
If it's marked 16 amp, it can't go on a 13 amp plug.
If it's 2.35 kw then it should draw around 10 amps.
Bosch appliances normally are hard wire connect only.
You could wire the oven and hob together if the total load is less than the 30 amp supply.
Check the hob for the total KW on the label of it.
If the total load of the hob and the oven are less that 6.9kw, you can wire them into the 30 amp supply.
Hope this helps
let me know how it goes or if you need more help
my hob is a neff and it is 6.600 kw, my single oven states on the back that it is 2.35 kwh cant understand why it is a 16amp not a 13amp
You can't run both off the same supply.
The hob alone is around 28 amps.
Sorry, you need to run another supply for the oven.
There is only 2 amp spare on the circuit.
It does state in the installation instructions that you should not connect the oven using a 13 amp plug or protect it with a 13 amp fuse.
thank you for your help you have given me different advice than I had about combining both on the cooker outlet 3 others have said it is fine to connect oven and hob together,
i will get electrician to fit it.
Sorry, I see the potential load as a maximum of 38 amps.
You have a 30 amp switch, which I assume is on a 30 amp circuit.
Good luck with it.