Ask A Question
HVAC Questions? Ask an HVAC Expert for Answers ASAP
White Rodgers Thermostat Problems
helps to adjust the temperature to a desired level in a particular system, according to a number of programmed settings. Thermostats help to arrest losses of heating and cooling in a building when the temperature rises and falls at different times during the day. White Rodgers thermostats are just one brand on the market today. However, thermostats can often malfunction and cause a person to have questions regarding the repair. Here are some of the frequently asked questions answered by Experts regarding White Rodgers Thermostat Problems.
If the screen of a digital White Rodgers Thermostat suddenly goes dark even though the functions work but am unable to change the settings and the batteries have been replaced, what could be the problem?
If the functions still work, it would seem that there is nothing wrong with the batteries. However, if the functions work even though the display doesn’t, it is more than likely because of a defective thermostat which you will have to replace with a new one.
How would someone get a White-Rodgers Thermostat Model which controls a gas-forced air HVAC system that the screen goes blank and has stopped heating to work?
The first thing to try is to open up the front cover and access the terminals marked R and W. It is possible that a low voltage fuse in the furnace has burnt out, but most probably, the thermostat seems to be broken. Bend a paper clip to “U” shape and have the terminals contact each other through the red wire terminal marked R and the white wire terminal marked W, which would help the furnace to switch on. This will function as your switch till you get the thermostat to work. Leave the wire as it is till the house is heated to your comfort level and remove it when you want the furnace shut off. You will have to operate it in this manner till you have a technician or Expert come fix the thermostat.
How would a White Rodgers Thermostat be disabled to be able to operate it manually?
In most situations, one could press down the “Hold” button and set the temperature as desired and keep adjusting it accordingly. This will help unless you press the “Run” button which will enable the program mode again.
If a White Rodgers thermostat is stuck in the “Hold ”position is there an online manual that can be referred to fix the problem?
First try removing the batteries and putting them back backwards for about 15 seconds. Take them out again and replace them in the correct position. This action sometimes helps to get it to reset. If this does not solve the problem, press the “Up” and “Down” keys at the same time which should help. The following link will take you to the instructions manual. http://s3.pexsupply.com/manuals/1249544570102/White_Rodgers_1F78-151_Instructions.pdf
If a White Rodgers Thermostat model number 1F83-277 that incorrectly reads 19 degrees inside the house when it is 82 degrees outside how can the thermostat be fixed to read the correct temperature inside the house?
The first thing is to try a hard reset of the thermostat. The following link will take you to a manual where you can look up “Troubleshooting” on page 8. Alternately, you could try taking out the batteries and replacing them after a few minutes. If none of these work, you may have to replace the thermostat itself. http://www.emersonclimate.com/en-US/resources/faq/white_rodgers/Documents/0037-6509.pdf If you own a White Rodgers Thermostat which runs into problems, or if you have doubts regarding its functions, you could always ask an Expert for solutions to your particular problem or clarify doubts you may have rather than trying to solve the problem yourself. Many times asking an Expert can help save time and money.
Recent White Rodgers Questions
I have a lp gas log set.Called the gas company, they said
I have a lp gas log set.Called the gas company, they said gas valve is bad. I have it off. it has on the valve WR monel746 type 201-e1 can1-6.4 can-9.1 ans z21.78 1/2 psi do you know where I can get this thank you
I have York two-stage gas furnace with single stage Honeywell
I have York two-stage gas furnace with single stage Honeywell digital thermostat. Second heating stage delay is controlled by a timer on the circulating blower housing.
Furnace totally quit, and I found a couple of cracked solder joints on controller board. After reassembly, furnace would only run maybe 5 minutes then flame would shut off with a 3 flash error code (Pressure switch stuck open.) An ohmmeter showed the pressure switch to be closed when running, and even jumping the pressure switch (the low-fire switch) with a clip lead would not keep it running more than five or six minutes. (house temperature now down to about 51 degrees).
I took the controller apart again... more futzing, and reassembly. Now it will run for about 10 or 11 minutes, right up to when the delay-timer switches to second stage. The burner goes to high, the inducer fan seems to run faster (hard to tell), and the blower fan speeds up. I runs like this for maybe 15 seconds and shuts down... i.e., the gas shuts off, with same 3-flash error code. It does this even though I jumpered the high-fire pressure switch!! (Low-pressure switch shows about 0.8 ohm resistance when running, high-fire switch shows about 2 ohms when running.)
At this point, I disconnected the 2nd stage timer, and the furnace seems to behave ok on the first stage only.
Question(s)... (1) does the second stage delay timer work purely on time, or is also a function of blower housing temperature? (2) I am suspecting that the controller is going bad... like maybe one or more of the relays can't handle the extra current of the second stage operation, or what? Maybe you can offer an explanation of what is likely failing.
i am installing an S861OU ignition control -honeywell- in lieu
i am installing an S861OU ignition control -honeywell- in lieu of a 50D5-843 white rodgers which replaced aG600AX2-original installation...transformer has a blue wire and a yellow wire going to control board terminals 1thru 5.....my question is what wire goes to 24 v GRD and what wire goes to TH-W? I have no vent damper
View More HVAC Questions
6 HVAC Technicians are Online Right Now
Ask Your Own HVAC Question
Ask Your Question Now
Ask a HVAC question
Type Your HVAC Question Here...
6 HVAC Technicians are Online Now
In The News
How JustAnswer Works:
Ask an Expert
Get a Professional Answer
Ask Followup Questions
100% Satisfaction Guarantee
Ask a HVAC Technician
Get a Professional Answer. 100% Satisfaction Guaranteed.
6 HVAC Technicians are Online Now
Type Your HVAC Question Here...
Disclaimer: Information in questions, answers, and other posts on this site ("Posts") comes from individual users, not JustAnswer; JustAnswer is not responsible for Posts. Posts are for general information, are not intended to substitute for informed professional advice (medical, legal, veterinary, financial, etc.), or to establish a professional-client relationship. The site and services are provided "as is" with no warranty or representations by JustAnswer regarding the qualifications of Experts. To see what credentials have been verified by a third-party service, please click on the "Verified" symbol in some Experts' profiles. JustAnswer is not intended or designed for EMERGENCY questions which should be directed immediately by telephone or in-person to qualified professionals.
Become a Professional
Terms of Service
Privacy & Security
© 2003-2015 JustAnswer LLC