Ask A Question
HVAC Questions? Ask an HVAC Expert for Answers ASAP
Air Conditioner Questions
What is an air conditioner?
An air conditioner is a device that heats or cools the air circulating in a room so that a comfortable temperature is maintained. Many air conditioners also control ambient humidity and filter out dust and dirt from the circulating air. Common air conditioner problems include the required temperature not being maintained, water leaking from the unit, inadequate air flow and the unit switching itself off when it is not supposed to or the air conditioner not working at all. Below are some of the most common questions on air conditioner problems that have been answered by Experts.
What could be LG Multi Type air conditioners problem if it is running water and dripping into the room? How can I fix this air conditioner issue?
The first thing to do is check if the indoor coil is level across the bottom. If it is, the most likely cause is a clogged drain hose. Disconnect the hose and blow or vacuum out any blockage. If the problem still persists then it could be due to a cracked drain pan which you can remove and check. Start by removing the 5 screws that hold the plastic front in place. The plastic dogs that are cast into the catches at the top and sides to hold the front in place can be loosened by spreading the sides apart slightly. The front will swing out and can be lifted off. You can now access the drain pan to check for cracks and leakage. Make sure that before lifting the front off you decouple the links to the air swing dampers to prevent any damage to them. If you are not comfortable doing this yourself, it may be better to call in a service technician.
My air conditioner has stated making a loud buzzing noise every few minutes from the fan or just below it. What could be the air conditioners problem?
The most likely causes are a compressor or fan problem. The noise could be coming from loose compressor bolts or because the compressor is straining due to a low refrigerant charge. The capacitor should also be checked to see that it is operating within range. If the noise is from the fan, it could be caused by an imbalanced fan blade. These are checks and repairs best done by a qualified service technician.
My air conditioner problem is that the unit is on but there is no air flow. The blower is running but the coolant line is covered with ice. What should I do?
First check the filter and if it is dirty or damaged, clean or replace it as needed. Next you need to turn the outside unit to the off position and turn the blower on. This will help to melt the ice. Continue with this for a few hours even after the visible ice has melted – there may still be ice inside the cooling line or the coil which will take some more time to melt. Once all the ice has melted start the cooling. If there is cold air flowing, the problem should be solved. If the problem persists, the cause may be a loss of refrigerant which will have to be replaced. This will require the services of a qualified service technician.
I have a problem with my GE portable room air conditioner model APH10. Water is leaking on to floor and the warning light that is supposed to come on when the drain pan is full does not light up. What is the problem and how can I fix it?
It appears that the unit is not sensing that the drain pan is full. If the unit has a float to sense the water level, check to see if it is sticking due to dirt or mineral deposits from the accumulated water. If this is so, clean the float to allow for smooth movement. If this does not solve the problem, check the drain pan for leaks and replace it if required. If there is a drain hose connected, check it for blockages and clean it out if required. Please keep in mind that if the air conditioner is running in very humid conditions the water collection in the drain pan maybe more than the unit’s ability to evaporate it, leading to the overflow. This should be mentioned in the instruction booklet.
My air conditioner problem is that my Carrier unit which is part of a Unico high velocity central air system does not work. The fan does not turn and there is no sound from the unit.
Check inside the air handling unit to find the “wet switch flood detector” and the low voltage float switch. Remove both from the drain pan. Dry out the pan, the flood detector and the float switch and put everything back in place. Check the drain hose. Find where it comes out of the building and vacuum out the line. The unit should now work.
An air conditioner is a complicated and expensive piece of equipment. Check the Owner’s Manual before attempting to repair any air conditioner problems to prevent injury or equipment damage. If the manual is not available or does not cover your air conditioner issues, you may need Expert help.
Recent Air Conditioner Questions
I have a Friedrich through-the-wall air conditioner, model
I have a Friedrich through-the-wall air conditioner, model SQ06N10A, which we bought just last year. I went to turn it on this year and while the power comes on and the control panel displays, the fan won't blow. We have the temperature down, the fan on Continuous, and have cleaned the filter.
I have an Amana GUCA115BX50 furnace, I had to replace the circuit
I have an Amana GUCA115BX50 furnace, I had to replace the circuit board about two weeks ago because the air Conditioner wasn't working nor the furnace, troubleshot, found circuit board bad, replaced circuit board, tested heat and air all worked, ran air works still however when switched to heat the board flashes three times, I checked drain and pressure switches and they seem fine, is there a way to test exhaust fan?
My 3amp fuse on my contro, unit keeps blowing. I've traced
Hi, my 3amp fuse on my contro, unit keeps blowing. I've traced the issue to the low voltage wiring coming from the outside A/C unit. Now I'm not sure if it is the wire itself shorting or something on the A/C unit, like the capacitor. Any advice on what is common to cause the 3a fuse blowing and how to check the wiring and components on A/C unit?
View More HVAC Questions
1 HVAC Technicians are Online Right Now
Ask Your Own HVAC Question
Ask Your Question Now
Ask a HVAC question
Type Your HVAC Question Here...
HVAC Technicians are Online Now
In The News
How JustAnswer Works:
Ask an Expert
Get a Professional Answer
Ask Followup Questions
100% Satisfaction Guarantee
Ask a HVAC Technician
Get a Professional Answer. 100% Satisfaction Guaranteed.
HVAC Technicians are Online Now
Type Your HVAC Question Here...
Disclaimer: Information in questions, answers, and other posts on this site ("Posts") comes from individual users, not JustAnswer; JustAnswer is not responsible for Posts. Posts are for general information, are not intended to substitute for informed professional advice (medical, legal, veterinary, financial, etc.), or to establish a professional-client relationship. The site and services are provided "as is" with no warranty or representations by JustAnswer regarding the qualifications of Experts. To see what credentials have been verified by a third-party service, please click on the "Verified" symbol in some Experts' profiles. JustAnswer is not intended or designed for EMERGENCY questions which should be directed immediately by telephone or in-person to qualified professionals.
Become a Professional
Terms of Service
Privacy & Security
© 2003-2015 JustAnswer LLC