Pool and Spa
Questions about Pool Repair? Ask an Expert Online.
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can continue our conversation.
Since you ran out of gas there's probably air in the gas line which is why you have an ILO (ignition lock out) error. To purge the air you need to power the unit down wait a minute then power it back up again. You may need to do this many times to get the air out. There is a quicker way but it involves taking the gas piping apart. Let me know if you'd like instructions for the quicker way.