I have a aqua rite salt water clorination system. the power and clorinating indicaters keep turning off for about a miniute then comes on about a miniute and continues this cycle.What could be causing this. Was working fine two days ago Roland Morvant
turning system off for 20 minites and restart
Hi My name is Garry
try doing a diagnostic
With the pump runing, go from "OFF" to "AUTO"
Press the diagnostic button two times
what voltage are you reading on the display?
Im getting a very erattic readings from 1.2-17.9
You should be reading a voltage between 24 to 31 volts.
Low voltage will require replacement of control board
Checking for response