Plumbing Questions? Ask a Plumbing Expert.
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can continue our conversation.
Far left and C LED lit is a flammable vapor sensor error. So if the sensor got wet you need to replace it. 150 k ohms indicates a failed sensor.Also it sounds like you'll have to pull the burner out and empty out the tubing to the burner it's probably full of water.