Plumbing Questions? Ask a Plumber and Get Answers ASAP.
Hi my name is ***** ***** I'm here to help you out. I see your question has been open and unanswered, and being an HVAC expert having installed many R.O. Systems for equipment protection, we can get you straightend out. Remember, Please do not rate your question until you are completely satisfied and all issues are resolved or the system will close your session!
What sounds like your issue is water volume. I have a few questions for you: 1) how long ago did you replace all of the filters? (There is a "purge" that will need to be done to move all of the air out of the system since it was opened - since the RO filter membrane is very fine, it may take a while for the air to remove itself.) 2: The water inlet connection may be partially clogged with build up (calcium, iron) causing the RO system to fill with water slowly, thus causing a reduction in volume - check to make sure all water connections are free of blockage 3: do you have a storage tank on your system? If so, verify the tank is filling with storage water and the inlet and outlets are not blocked with debris 4: check the manifold connections to make sure they are not blocked with debris either.