Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can continue our conversation.
Sounds like your boiler needs to be cleaned. It sounds like it's clogged with soot which is an indication of inadequate air for combustion. You also need to address the combustion air issue or this will happens again.
You're welcome. You also have to address the combustion air problem
Flame is probably rolling out and tripping the rollout sensor or the heat diverted because of the soot is tripping it.