Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can continue our conversation.
Yeah I'm not buying it either. 140 is too hot for a radiant panel (floor) typical water degign temp is always less than 120. You should have a tempering valve on the radiant loop that will recirculate water in thefloor until it cools down enough to circulate back to the boiler. Sounds like your guy isn't real experieinced with radiant systems.