Have HVAC Questions? Ask an HVAC Expert for Answers
Hi, how are you? Can you tell me which component each of those wires are running to? I have pulled a diagram up but that's a replacement module and I want to make sure that the wires are the same and haven't been altered through servicing. Thanks
Ok, Red, you said you are certain is MV, Blue should be on PV on the valve and PV on the controller. Is there a mv/pv terminal on your gas valve?
Trace the brown wire back and tell me where it goes to
The gas valve doesn't have any labels? Can you get a model number off of the valve for me?
Wire the brown to TH
Can you take a picture of the wire terminations on the gas valve for me?
PV from the controller should wire to PV on the valve and MV to MV and then you should have a common connection.
You have to have a common wired to the gas valve. So I think your orange is your common. There should be a terminal on the controller labeled flame sense.
wire orange to the MV/PV terminal on the module
Try to run it.
I need to opt out as I have an unexpected situation arising at home. I apologize for the inconvenience. There should be another expert shortly to assist. Thank you for your understanding.
does this look like your wiring?
It is how the unit was wired new...click here
There are 2 greens that I see...the one hanging loose....what does other end go to?
I see a green on G which should come from stat
does this look closer? click here
and here is about spark after pilot lit...click here
ok, terminal 6....what wire is attached and where does it go?
And if you can bear with me...
On terminal R where thermostat wires attach...there are 2 reds. One goes to thermostat..where does the other go?