Have HVAC Questions? Ask an HVAC Expert for Answers
Hello, my name is ***** ***** I look forward to helping you!
This sounds like a pressure switch stuck open
Leave on end of th hose connected to the pressure switch and blow then suck on it. Does it click?
I am Tim a different expert, The 3 flash code indicates pressure switch is CLOSED and inducer is OFF.
The inducer should run non stop until call for heat is satisfied.
Is the inducer quitting? And are you sure the code is 3 flashes?