Have HVAC Questions? Ask an HVAC Expert for Answers
see page 3 HERE
Is this the wiring you need?
do you mean the blower motor red and black as shown in the diagram HERE on page 3?
Picture has not come through yet.
If you have a paper clip icon on your page you can attach using that link.Or
You can upload the pictures using the tiny pic site .
Here is a link to the site.
Click on Browse , select the file from your folder.then click UPLOAD NOW.
They will give you a quote to enter in the box to verify you are a human.Enter the quote and click UPLOAD NOW
You will see your picture on right side of screen.
Then copy the link URL for email & IM
Paste that link here on the site.
Try attaching pic here following these instructions.
Sorry but it may be a glitch in site somehow,Are you copying the link and pasting here in chat?
I hope I can get the photo .Really want to help.
The website blocks direct emails so we don't establish a relationship outside if the website.
Are you talking about the high voltage black and red from transformer?
Red should go to pin 13 and black should go to pin 14 on the 15 pin plug.This supplies 240v to the heat kit.
Try taping the red and black separately and see if furnace will work.This should be the only power wires you need to heat kit.
Look forward to hearing back
Got the one that says screenshot.
that black and red should be connecting to the heat kit.Do you have heat kit connected somewhere else?
That is correct according to wiring diagram. So are there other red and blacks that you were referring to touched cabinet and sparked?
Can you send a pic of where they come from and tell me if they are factory wires?
OK we will go from there. Lets do what I mentioned about taping them off and see if everything works.
Fan should only use 2 wires.
Hmm that diagram said 3400 and 3500
Shows the fan wires connecting to pins 2 and 6 on the 15 pin plug
2 and 6
My diagram shows the heat kit wired to pins 13 and 14 in the 15 pin plug and the blower to pins 2 and 6. I have sent diagrams for both.Going to be out of office so I will open to other experts
Do you need more help?