Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can continue our conversation.
You either have an underlying expansion problem or a problem with the feed valve. If the pressure rises to above 30 psi when the boiler is cold and not firing then the feeder is the likely culprit. If the pressure rises to over 30 psi when the burner is firing then you have an expansion problem most likely due to a failed expansion tank.
Do you have more questions?