Have HVAC Questions? Ask an HVAC Expert for Answers
What is the model you are getting the error code on?
Not familiar with the model,Will open to other experts
This is a error that the ignitor has cracked or shorted to ground. This is a situation where you must access the ignitor at the burner rack and see if cracked or broken and replace.
There is not much troubleshooting for this failure and is not related to a water pipe failure...UNLESS the water actually got on the ignitor during use.. which means the ignitor still replaced anyway.