Have HVAC Questions? Ask an HVAC Expert for Answers
My name is Billy.
If the heaters engage but not the blower then you have a bad sequencer switch. The sequencer is a stacked switch...first blower starts, then one bank heaters...then 2 or 3 if present...
If motor is good then the issue is sequencer relay
Follow the black motor wire...the item it goes to is what is bad.