Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. First I’ll need some more info so I have a more complete picture of you situation.
Does error occur before ignition tries or after 5 ignition tries/atempts?
Could be a bad connection to the gas valve. Also check the resistance across the outer 2 pins on the gas valve. Should be ~50 ohms. Resistance across each pin to ground should show an open circuit
If readings are not in this range then replace the gas valve. If they are OK then you probably have a bad control module.