Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is Luke
NOTE: I can only get paid for assisting you if you RATE ANSWER the 5 star rating when we are done
Are you ready?
Two blinks indicates the pressure switch is not closing. Does the small vent motor come on as soon s you call for heat?
OK next do this. Take the hose loose from the inducer and leave attached to the pressure switch.Start furnace and as soon as inducer vet motor starts, begin sucking on the hose and see if pressure switch will close and ignite furnace