Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. First I’ll need some more info so I have a more complete picture of you situation.
Are you sure about that model number? could it be an NUGK...?
I'm not finding that model in the database. The only resets are the rollout switch/sensors (see attached pic for typical) located just above and outside the burner chamber. If you push the small button between the 2 wires and it clicks you have reset it. If it doesn't click it wasn't tripped. One other possibility is the blower compartment panel switch. If the access panel to the blower compartment is not securely in place it won't engage the plunger type switch behind the panel and the unit won't get any power. Of course all service/emergency switches should be on. You can also check the breaker. If you replaced the thermostat without turning the power off to the furnace you could have fried the transformer.
Probably explains why I can't find any specs on it. Can you give me a picture of the inside of the burner compartment? If it has a wring diagram and you can do some additional troubleshooting give me a well focused picture of that too. It's usually pasted to the inside of one of the access panels. You can post pics here by clicking on ADD FILES next to the SEND button